Fire Suppression Systems and Permit Application
The Naperville Fire Department is the authority having jurisdiction for permit issuance and acceptance testing and inspections of Fire Suppression Systems. This includes new systems and/or modifications/alterations to existing systems. Fire protection systems include, but are not limited to sprinkler systems, dry pipe systems, standpipe systems and Ansul Systems etc. All required fire protection systems must be approved by the Fire Department before the Development Services Team will issue an occupancy permit.
- Basements and mechanical penthouses, and areas under canopies, where vehicles have access, shall be included when calculating the building square footage.
Electrical Equipment shall meet NFPA 13 Section 126.96.36.199 "Sprinkler protection shall be required in electrical equipment rooms. Hoods or shields installed to protect important electrical equipment from sprinkler discharge shall be non-combustible".
Electrical rooms/closets and sprinklers shall not be required where all of the following conditions are met:
- The room is dedicated to electrical equipment only.
- Only dry-type electrical equipment is used.
- Equipment is installed in a two-hour fire-rated enclosure including protection for penetrations.
- No combustible storage is permitted to be stored in the room
The exempt locations must provide a fixed-temperature heat detector, separately zoned at the FACP.
Standpipe systems shall be installed in all buildings three (3) or more stories in height with common corridors exceeding twenty-five (25’) feet in length, and are required in each stairwell at every level. Standpipe systems shall be installed in all buildings which are four (4) or more stories in height including penthouses.
Standpipe systems shall be installed in all buildings where any portion of the building floor area is more than 400 feet of travel from the nearest point of fire department vehicle access.
Dry Standpipe systems are not permitted.
Fire Department Connection (F.D.C.) shall be a 5 inch Stortz connection. A 2 1/2 inch NST Single F.D.C. shall be acceptable where piped to a 3-in (76-mm) or smaller riser.
Fire Protection systems must be inspected at certain intervals according to the following schedule:
Fire Sprinkler Systems
Rough inspection of piping and flush test
Final acceptance/performance test
Trip/Dump test (Includes verification of fire panel zoning)
Final acceptance/performance test
Information is provided on the plan review comment sheet/form, included with your permit.
Inspections may be scheduled by calling (630) 420-6100 at least 72 hours in advance. When inspections are scheduled, all appropriate installers must be present.
The fee for all inspections is $61.
If an inspection/test fails, the Fire Department will attempt to accommodate the fire protection system installer’s request by scheduling a re-test the next business day. Any re-inspection/re-test will result in a fee of $61 per hour, one hour minimum.
Plans for each fire protection system must be submitted to the Development Services counter, Municipal Center, 400 S. Eagle Street, Naperville, IL 60540 for review purposes. Plans are generally reviewed and written comments provided within 14-21 calendar days. After the review is completed, the applicant will be furnished with at least one (1) set of stamped drawings, which are required to be on-site and available for the Fire Department inspector.
The plan submittal shall include:
A minimum of two (2) sets of plans for each fire protection system
Fire protection system calculations
Manufacturers specification sheets on all devices
Fire Protection System Application Form (download below)
The plan review fee must accompany the submitted plans. The plan review fee is $44.00 per page plus $.50 per sprinkler head plus $16.00 clerical fee, and the first inspection fee of $61.00.
If plans must be re-submitted the $44.00 per page plus $.50 per sprinkler head plus the $16.00 clerical fee must accompany the resubmitted plans.
When a fire protection system is being modified and such modification involves ten (10) heads/nozzles or less, the plan review fee includes one (1) inspection.
Fire protection systems must be designed and installed and function in accordance with locally adopted codes and locally adopted amendments to the codes. This information, and other general information regarding Fire Protection Systems and Fire Alarm Systems is available from the Development Services counter, Municipal Center, 400 S. Eagle Street. To obtain this information, call (630) 420-6070.