Fire Alarm Systems and Permit Application
The Naperville Fire Department is the authority having jurisdiction for the issuance of fire alarm permits and acceptance testing and inspection of Fire Alarm Systems. This includes new systems and/or modifications/alterations to existing systems. All required fire alarm systems must be approved by the Fire Department before the Development Services Team will issue an occupancy permit.
The Naperville Fire Department also provides guidelines and requirements for the installation, maintenance and testing of fire alarm systems in the City of Naperville.
Areas under canopies, where vehicles have access, shall be included in calculating the building square footage AND protected, if required.
When any building or a portion thereof is renovated or remodeled, automatic fire alarm systems shall be modified to conform with then-current Code requirements: Change of Use Group AND aggregate square feet of building or portion meets above areas. (If no change of Use Group however, the aggregate square feet of building or portion meets the above areas, automatic fire alarm systems shall be modified to conform with the then-current Code requirements).
Where a change in Occupancy includes any use which requires the entire structure to be protected with a fire alarm system, such a system shall be installed throughout the structure before an occupancy permit for the premises is issued.
Fire Department Key Lock Box: To facilitate Fire Department entry to a building, a Fire Department key lock box (model and type to be approved by the Fire Department) shall be provided adjacent to a doorway (Location shall be approved by the Fire Department). All keys placed in the lock box shall be tagged for property identification.
Fire alarm systems must be inspected at certain intervals according to the following schedule:
Fire Alarm Systems:
Rough wire inspection (Not required in all instances)
Final acceptance/performance test
Information is provided on the plan review comment sheet/form, included with your permit.
A contractor's Certificate of Completion (PDF) shall be provided to the Fire Department prior to the Fire Department witnessing a performance test of the system. (Per NFPA 72)
Inspections may be scheduled by calling (630) 420-6100, Option 1 - 48 hours in advance. When inspections are scheduled, all appropriate installers must be present.
The fee for all inspections is $68.
If an inspection/test fails, the Fire Department will attempt to accommodate the fire alarm system installer’s request by scheduling a re-test the next business day. Any re-inspection/re-test will result in a fee of $68 per hour, one hour minimum.
Plans for each fire alarm system must be submitted to the Development Services counter, Municipal Center, 400 S. Eagle St., Naperville, IL 60540 for review purposes. Plans are generally reviewed and written comments provided within 14-21 calendar days. After the review is completed, the applicant will be furnished with at least one (1) set of stamped drawings, which are required to be on-site and available for the Fire Department inspector.
The plan submittal shall include:
- A minimum of two (2) sets of plans for each fire alarm system.
- Manufacturers specification sheets on all devices
- Standby battery calculations
- Wire sample (6")
- Fire Alarm Plan Review Submittal Sheet (download at right)
- Fire Alarm System Application Form (download at right)
When a fire alarm system is being modified and such modification involves three (3) or less devices, (or Fire Alarm Control Panel) the plan review fee includes one (1) inspection.
Fire alarm systems must be designed and installed and function in accordance with locally adopted codes and locally adopted amendments to the codes. This information, and other general information regarding Fire Protection Systems and Fire Alarm Systems is available from the Naperville Fire Department.